- MILITARY-INDUSTRIAL COMPLEX: Defense Dept. Contracts for Aug. 29, 2014
- OP-ED: Michael Brown and America’s Structural Violence Epidemic
- CARIBBEAN VIEW: Scotland’s Independence: Does it matter?
- OP-ED: 'Who Speaks for Earth?'
- CARIBBEAN VIEW: No Caribbean Appetite for a Rum Fight
- OP-ED: In Ferguson and Beyond, Militarism Is a Public Safety Crisis
- Tickets to all Marshall Artists Series events go on sale Monday, August 18 @ Noon Call 304-696-6656
- Preventing Substance Abuse and Mental Illness
- DEVELOPING: Former MU Coach Perry Moss Dead
- BOOK NOTES: Book Signing Saturday Features Authors of 'Pretty Little Killers'
A second stormwater overflow discovered at Freedom Industries spill site
Friday, June 13, 2014 - 23:12 Updated 10 weeks ago Edited from a Press Release
Today's overflow coincided with a heavy downpour of rain at around 5 p.m. The discharge lasted for approximately 50 minutes before being brought under control through increased pumping.
The incident follows a similar overflow of stormwater discovered yesterday (Thursday, June 12). In that instance, the DEP determined a pump float level, meant to trip the device on, was not properly set. Two notices of violation were issued following that event: for allowing a discharge from an unpermitted outlet, and for failure to comply with the terms and conditions of an order to implement an approved sump management plan. NOVs are being issued for today’s discharge as well – and will include a mandate that Freedom respond by noon tomorrow (Saturday) with an outline of how the system will be redesigned to prevent future overflows.
The DEP inspector who discovered the latest discharge has relayed that the sump pump was operating, unlike yesterday's incident, but apparently could not keep up with the heavy flow of rainwater. A backup pump was activated to increase pumping capacity.
West Virginia American Water, which has a drinking water intake a mile and a half downstream, has been notified and will be collecting samples of raw water coming into the plant intake as well as treated water. Initial results are expected later tonight. Testing of raw and treated water samples after Thursday's discharge came back at non-detectable levels.
A 10,000-gallon crude MCHM leak at the site on Jan. 9 contaminated the drinking water of approximately 300,000 people. Construction of the trench was commenced that day so that rainwater and groundwater running across polluted soil at the site would not seep into the river.