- Q and A with Mayor Steve Williams: Audits ALWAYS have Findings....
- Marshall University Board of Governors to hold emergency meeting this afternoon
- Q and A with Councilman Caserta: Mayor Needs to be Held Accountable, Independent Audit Necessary
- Christmas Kente Ceremony for winter graduates is Saturday at Marshall
- FREDDIE MAC: Mortgage Rates Find New Lows for 2014
- Special Prosecutor Will Be Appointed in Cabell County Regarding State Police Investigation of Mayor's Sick Leave Payment to Skip Holbrook
- CFPB Takes Action to End Student 'Debt Relief' Scams; CFPB Warns Borrowers About Companies Charging High Fees for Free Federal Loan Repayment Programs
- Bid Specifics Revealed in Huntington Street Sweeping Program
- OP-ED: How About Another Christmas Truce?
- Huntington Buns on Bikes Race IMAGES
A second stormwater overflow discovered at Freedom Industries spill site
Friday, June 13, 2014 - 23:12 Updated 1 year ago Edited from a Press Release
Today's overflow coincided with a heavy downpour of rain at around 5 p.m. The discharge lasted for approximately 50 minutes before being brought under control through increased pumping.
The incident follows a similar overflow of stormwater discovered yesterday (Thursday, June 12). In that instance, the DEP determined a pump float level, meant to trip the device on, was not properly set. Two notices of violation were issued following that event: for allowing a discharge from an unpermitted outlet, and for failure to comply with the terms and conditions of an order to implement an approved sump management plan. NOVs are being issued for today’s discharge as well – and will include a mandate that Freedom respond by noon tomorrow (Saturday) with an outline of how the system will be redesigned to prevent future overflows.
The DEP inspector who discovered the latest discharge has relayed that the sump pump was operating, unlike yesterday's incident, but apparently could not keep up with the heavy flow of rainwater. A backup pump was activated to increase pumping capacity.
West Virginia American Water, which has a drinking water intake a mile and a half downstream, has been notified and will be collecting samples of raw water coming into the plant intake as well as treated water. Initial results are expected later tonight. Testing of raw and treated water samples after Thursday's discharge came back at non-detectable levels.
A 10,000-gallon crude MCHM leak at the site on Jan. 9 contaminated the drinking water of approximately 300,000 people. Construction of the trench was commenced that day so that rainwater and groundwater running across polluted soil at the site would not seep into the river.